Since the ECSPLC is now fully wired (06 May 2009) to support the new auxiliary temperatures and alarms, the appropriate changes have been completed in the ECS subsystem to support this functionality. Recall the new temperatures displayed on the ECSGUI Chiller tab are
Supply Auxliary Chiller Temperature
Return Auxliary Chiller Temperature The warnings and alarms will be indicated when appropriate:
Add a check for the AGW unit number in selectAGW so different AIP_LUCIFER units can be properly selected (IssueTrak #2164).
The automatic AGW selection has been disabled. THIS MEANS THE COMMAND LINE COMMAND, selectAGW config_file, MUST BE USED EACH TIME THE GCS IS STARTED.
For wavefront sensing, the X position of the probe is rectified (+/-1) based upon the WFS_pupil_shift_x parameter in the appropriate AGW file. There is also a rectification (+/-1) in the computation of angles based upon the WFS_pupil_shift_y parameter.
Replaced use of the dispatcherRPC with a standard RPC call to avoid the problem of the rotator polynomials getting "held up" when trying to transmit to the MCSPU when a "ready" on the rotator has been invoked.
If the ECS or ventilation blower is not running, override the mirror ventilation set point command value to be glass - 0.9C per John Hill's request (IssueTrak #1846). This is to prevent the set point from getting cockeyed during the day when the air is warm.